‘Stormsaver have always provided a quick response to any queries and their customer service is superb’
Project Estimator - Walter Miles
Here you'll find answers to most of the common questions people have about our rainwater harvesting systems. If your question isn't answered, please feel free to contact us, our team is always happy to help!
We have a huge wealth of information on rainwater harvesting available on our website and from us direct. If you can’t find what you are looking for on our website please contact us and we can provide information on our systems, personalised recommendations, quotes and much more. To get in touch call us on 0844 884 0015 or send us an email on firstname.lastname@example.org.
Rainwater harvesting is the process of collecting rainwater that hits the roof, or other flat surfaces. This rainwater is then collected in a tank which usually sits below the ground. When water is required in the house or building where the system is installed it draws the water from the external rainwater harvesting tank. Before the water is used it is filtered and treated appropriately depending on what the water is used for e.g. flushing toilets, washing clothes or car washing etc.
For more information call us on 0844 884 0015 or send us an email on email@example.com.
Stormsaver has the largest team of Rainwater specialists in the UK. We have technical assistance available throughout the design, installation and commissioning process with a team of our own engineers - on hand to respond quickly to any queries you may have concerning your Stormsaver system. In the first instance please make contact our technical team on 0844 884 0015 who may be able to address your query over the phone.
Stormsaver offers a 1 year warranty from date of commissioning all component parts ordered – As a responsible manufacturer Stormsaver is on-hand to provide continued assistance and technical support throughout the installation and commissioning process…. And it doesn’t stop there ask about our service and maintenance packages - 0844 884 0015.
The main aim of any rainwater harvesting system is to produce non-potable water that is clean, clear and odourless. Two or three stages of filtration take place to ensure the water is clean and clear prior to it reaching any non-potable appliance, depending on your specification.
If you have dirty water it is unlikely to be the system not operating correctly and is more likely to be dirty filters, dirt in the tank, or dirty water entering the system by accident from another source.
Contact our Rainmaintain team on 0844 8840015 and they can help you figure out how to fix it!
Stormsaver do not recommend rainwater be used for drinking. From a health viewpoint it is not worth the risk of drinking untreated rainwater. Also the additional cost of installing equipment and maintaining and testing filtration and disinfection required to achieve Drinking Water standards is not economically viable. There are lots of Non-drinking applications where filtered rainwater can be used and achieve the same percentage of overall system efficiency over an annual period. See how it works.
Here are a few of the non-drinking applications that you can use your recycled rainwater for:
Stormsaver recommend that you carry out a risk assessment for each site and application. Certain applications may increase the likelihood of accidental ingestion or breathing in the vapour from the rainwater as an aerosol - e.g. created by spraying water such in a vehicle wash, wash down facilities, spray irrigation. Other installations where disinfection should be considered due to there being young, elderly or those with low immune systems this may include schools, hospitals, health centres, care-homes, or HM Prisons.
A grey water system uses dirty was collected from Baths, showers, washing machine but normally excludes water from the kitchen sink. Water in a grey water system can fluctuate in water quality depending upon the source of water and it is normal practice to only store small volumes of water for up to a 24 hour period to prevent rapid growth of bacteria. The water may contain faecal contaminants from washing machines or from bathing water from children, detergents, skin deposits, body fats, hair etc all of which require removal and disinfection prior to application. Check out our rainwater harvesting products.
Stormsaver do not recommend mixing greywater with the filtered rainwater.
Stormsaver can supply a range of monitoring packages from simple metering through to integrated display screens providing live data on system operations – all options can be linked to your BMS will the intelligent Stormsaver control system. Stormsaver will monitor the water demand for you during our maintenance contracts! Harvesting Specification Tool
Tanks are sized on a two week demand period, which according to the MET office is the average period the UK experiences without rainfall. If the site is to be assessed by BREAAM an assessment method is used following the recommended requirements. Free assessments are available through the Stormsaver estimating department, or by downloading an assessment form. It is essential to have details of the site location, roof area, proposed applications, number of appliances and number of people within the building. Check out our rainwater harvesting products.
The depth on site can be variable depending upon the depth of the drainage on site. A standard tank can be installed with up to 2.0m of cover. Tanks installed below this depth will require a heavy duty tank or super heavy duty depending upon depth and the height of the water table. Check out our rainwater harvesting products.
There are no Building Regulations concerning the position of a Stormsaver system, however good practice would state that the tank must be positioned at least 5m away from a building. Please notify Stormsaver (0844 8840015) of the length of pipe run from the system controls to enable us to provide the correct size of pumps to achieve the desired flow rates taking into account pipe sizing. Check out our rainwater harvesting products.
Stormsaver standard tank range should be encased in concrete. Stormsaver do offer a range of larger tanks suitable for installation in pea gravel however the installation is more involved due to surface loadings and the height of the local water table, allowance for surface water within the ground etc. This makes this option economically viable for larger tanks – smaller tanks may be better installed by concrete surround – ask our technical team 0884 884 0015
Yes, Stormsaver tanks can be buried below the water table – allowance is required for de-watering the excavation during installation and details of this are supplied with the system or from our technical team 0884 884 0015. Check out our rainwater harvesting products.
Yes, it is a requirement of BS8515-2011 to filter the water prior to storage. This first stage of filtration is critical to assist with water quality. Why choose us?
Stormsaver provide a range of above ground tanks as single piece tanks – cylindrical or rectangular or tanks built as sectional in construction. Check out our rainwater harvesting products.
Yes the tank can be installed in a car park or driveway, however the installation must ensure that surface loadings cannot be transferred onto the storage tank (drawings supplied). If the tank is installed in a HGV park it is advisable to protect the tank using a reinforced concrete slab over the installation and surrounding ground. In any case it is always advised to seek the advice of a structural engineer. You may need to specify a heavy duty tank depending on the depth of installation
All rainwater harvesting supply pipework should be in WRAS approved black and green or clearly identified with black and green tape. Under no circumstances should pipework from the tank be run in blue.
The electrical connection chamber is used to terminate pump connections and install isolators. It is not recommended to fit the connections within the tank / pump chamber. The isolators are required to locally isolate power to the pumps during maintenance. How it works.
The water pressure delivered into the building is normally between 3.5 -4.5 bar, however this is dependent upon the length of pipe-run, size of pipework, height in metres from the pump to the building – if larger or smaller flows and pressures are required we can supply pumps to suit the location to ensure you have the correct flow rates and pressures required. Ask our technical team on 0844 884 0015 and we can help you through this process to ensure you have the correct equipment. Check out our rainwater harvesting products.
In order to obtain the most efficient system, it is important to understand the length of pipe-run, size of pipework, height in metres from the pump to the points of use to correctly size equipment to the correct flow rates and pressures required. Ask our technical team on 0844 884 0015 and we can help you through this process to ensure you have the correct equipment
A header tank is one option for the installation of the Stormsaver system, however not all buildings can fit a header tank in which case Stormsaver can supply a Combi unit or a direct pressurised system depending the water demand of the building and site requirements. Our sales team can help you choose which type of system is best call them on 0844 884 0015. Installation
Yes, with a Stormsaver system a range of individual tanks can be installed around the building – up to seven in total with a standard d unit. Should more be required Stormsaver can supply a bespoke package for additional tanks.
A header tank can be fitted anywhere in the building. If it on the ground floor or basement level a booster pump can be used to distribute the water to points of use – rather than the use of gravity direct from the tank.
A header tank can be fitted on the roof of a building – if this is the case we would recommend increasing the insulation from the standard 25mm up to 50mm to prevent freezing or warming. Any pipeworks to the tank also require insulation and or trace heating. Check out our rainwater harvesting products.
In a Non-pressurized header tank system mains water back up is fed directly into the break tank. For a Pressurised system the mains back-up is fed into the underground storage tank. The combi unit has a mainswater top-up directly into the unit – in all cases this connection is made via a WRAS approved Regulation approved airbreak. Installation. For help choosing which type of system is best for your site ask our estimating team on 0844 884 0015
The tank with its integral leaf filter will be delivered to site ready for installation. The remainder of the mechanical equipment such as pump components, header tanks are usually required at a later stage and will be delivered to suit your build programme – these can be called off later minimizing your risk of damage, loss or theft of these costly bits of equipment. It is the contractors responsibility to ensure suitable lifting equipment is prepared on site to take delivery of the tank, header tank, COMBI unit or any other large or bulky items such as booster sets. Please contact technical team on 0844 884 0015 to discuss the exact requirements. Installation
Each Stormsaver system has a common alarm to connect to the BMS as standard, however we can upgrade this option if required to provide signal readouts for low level contents, contents 0-100%, pump operation, pump run time, flow rate, flow in litres for rainwater and mainswater, filter clean operation, UV disinfection alarm, low flow… if these aren’t enough ask our technical team on 0844 884 0015 and we can add other bespoke items such as temperature, high level alarms etc to your specification. Installation
Yes the Stormsaver system comes with visible alarms on an LCD screen sited on the front of the Stormsaver Processor unit. This shows you clearly what the system is doing…. it may be that it is just waiting for you to use water. The unit has a range of alarms such as flow rate, water used in litres, pump operation, pump fail and can show when filter maintenance is required. If you upgrade the system the system can even backwash these filters for you to minimize maintenance requirements and provide peace of mind. If the visible panel and alarms aren’t enough, the system is easily connected to the BMS.
Stormsaver provide a free site visit to advise on the installation taking into account any site specific requirements. Contact us today
It is recommended that when piping up the rainwater system that a different pipework material is used on the rainwater pipework to the mainswater pipework, this is to avoid accidental cross connection of the two supplies at a later date. Stormsaver can provide WRAS approved pipework identification tape to apply to pipework to avoid any confusion of the contents and it is a requirement that that this is used.
Yes, internal pipework within the building should be insulated, any pipework installed externally if above ground should be isolated or trace heated to prevent freezing or warming.
Once the system is installed Stormsaver carry out the commissioning of the system to ensure trouble free operation. We use only use our own engineers giving you peace of mind that you always have a specialist to hand. Maintenance Packages
Stormsaver are manufacturers of Rainwater Harvesting systems, the installation should be carried out by your own contractors. Stormsaver provide a free site visit to advise on the installation taking into account any site specific requirements. Once the system is installed Stormsaver complete the commissioning of the system to ensure trouble free operation. Check out our previous work. Our technical team are always on hand to offer assistance 0844 884 0015.
Yes the Stormsaver system is ideal for this, as all roof water can be directed to one outlet which is connected to the Stormsaver tank, therefore reducing additional pipework and ground work costs. How it works. It is important to understand the large flow rates and velocity of the water in a syphonic system and a vented siphon break is required prior to the filtration unit and storage tank ask our technical team on 0844 884 0015
Stormsaver provide a complete Operations and Maintenance manual including any site specific drawings of equipment fitted at the specific site. The manual provides a breakdown of maintenance, which can be carried out either with your own maintenance team, or we can take out the hassle for you and maintain the system with our range of maintenance packages based on 1-5 year contracts. Why? Ask our service team on 0844 884 0015.
The system has a visual alarm on the panel to advise you to clean the filters. If you upgrade the Stormsaver system the filters in the building can even backwash these filters for you to minimize maintenance requirements and provide peace of mind. If the visible alarm isn’t enough, the system is easily connected to the BMS. Tank Cleaning
Rainwater is free from detergents and is soft water (ie no limescale), along with other applications this makes it ideal for use in washing machines on the garden and when washing the car you will not get the smears left by scale from mains water! Tank Cleaning
Yes the rainwater is soft water and free from detergents, it's great for using on your garden and for other outdoor uses including washing cars, jet washing patios etc. It is always recommended to fit a locking tap and labels to prevent accidental ingestion or cross contamination of water supplies. Benefits
Find out more about using recycled rainwater on your garden.
WRAS Approved labels can also be supplied to mark items such as taps, toilets and urinals etc so that people are aware that they are using rainwater. Good for ‘awareness’ as well as preventing accidental ingestion. It may be required for all appliances to be cleared marked as being supplied by rainwater.
‘Stormsaver have always provided a quick response to any queries and their customer service is superb’
Project Estimator - Walter Miles